S7-Interface cable for PPI, MPI, Profibus, HMI <=> LAN applications
- Supplied driver TIC (Total Integrated Communication) (runs under Win XP, VISTA, Win7/8/8.1, Win10) allows communication and configuration of the interface product
- Function with TIA-Portal and Simatic-Manager, also with WinCC and Comfort Panel
- Automatic protocol- and baud rate detection (depends on the used product from 9K6 to 12M)
- Connects only to the bus when it is requested by PG
- Firmwareupdate via internet for free
- PPI - adapter for S7 - 200
- MPI/Profibus - adapter for S7 - 300 + 400
- CE/EMC compliant construction
- All intelligent MPI-interface-products including a free OPC-server license "OPC-Manager lite" [limited to 100 items]
- All products, including the examples and demo-version of communication driver as download on the product-site
- Master-class 2 for acyclic services (DPV1)
- PUT/GET from S7-1500/1200/300/400(PN or with ethernet-cp) with spezific and unspezific connection possible
- Cyclic read of time from NTP server and set in the connected PLC
- Coupling with DB-transfer to S7-LAN, S7-Gateway, S7-CP, S5-LAN++ or S5 Gateway
- Power supply from the S7-PLC or external
- Network configuration free adjustable
- VPN remote maintenance possible / for the maintenance of the PLC via Internet
- Integrated display for output of diagnostic informations
- Double-sided connected cable
- Short plug to PLC
- Provides the coupling with Android operating-system [for example S7Droid]
|Supply voltage:||24V/DC +/- 20%|
|Power consumption:||2,5 watt|
|Display:||double lined LCD-display|
keypad on the back
to the PLC:PPI/MPI/Profibus interface: 9,6 KBd - 12 MBd
to the PD/PC:10/100MBit ethernet interface
|Galvanic separation:||1500V PPI/MPI/Profibus to the PC|
|Operating temperature:||5 - 55°C|
|Dimensions:||146 x 41 x 29 mm|
|Scope of delivery:|
Power connector 2pins small
Programming of S7-PLCs via LAN
You would like to respond to your S7-PLC-device via LAN but not integrate an Ethernet-CP? No problem, plug the S7-LAN or also the MPI-LAN-cable on the MPI/PPI/Profibus-interface and access via LAN.
Watching of S7-PLC-devices via LAN without Ethernet-CP
Your panel only has a LAN-socket as PLC-interface? No problem, connect this socket with the S7-LAN or the MPI-LAN-cable and plug it directly on the PPI/MPI/Profibus of the PLC. Then access to the variables and data of the PLC is already available.
S7-CP-replacement (without LAN-CP to the PLC-device)
Do you have a S7-PLC-device without CP243-1, CP343-1 or CP443-1 and would like to connect via LAN? Then plug the S7-LAN on the PLC-device and your access via RFC1006 is ready for use.
Remote maintenance / telecontrol of PLC-devices via LAN / internet
You have access to a on-site network and your PLC-device has no LAN-connection? No problem, plug the S7-LAN on the PLC-device and you will have immediate access to the PLC from afar.
Without LAN-cable round of the PLC
Your’re right in the middle of your production line and and should move around the machine and simultaneously observe / manage. No problem, you parameterize the S7-WLAN-Bridge, connect to the MPI-LAN and connect to an access-point or with the ad-hoc-network of your laptop and are ONLINE on the PLC.
Transformation of Rack/Slot in TSAP to MPI-address
Your panel or visualisationsystem addresses the used PLC with Rack/Slot in TSAP? No problem, activate this mode in the MPI-LAN-cable and you will get actual data from the PLC.
PLC-coupling (data exchange between PLC-devices)
Your pumping stations report the water levels of the central control via telephone network. The central office itself can of course transmit commands/messages to the substations as well. Thereto no dedicated line is required, it’s sufficient when the stations connect via network (DSL-router).
Actual time for the PLC?
You need in your PLC a actual time? No problem, with the NTP-function the MPI-LAN-cable get from a NTP-(Time-)Server the actual time and transfers it direct into the configured PLC or for processing in a DB.
Variable-chart without Step7-programming package
You would like to give your customer the opportunity to read current numbers of the manufacturing Online, without installing a visualisation or even the STEP7-package? Then a S7-LAN with the option „Status Variable“ is needed, and your customer can take a look at these password protected data on a site of the integrated webserver.
Malfunctions on the Bus although everything is (apparently) connected properly?
The S7-LAN can also be used for controlling/checking the MPI/Profibus. It will be plugged on the Bus so that you can take a look at the status of the busses via software on PC, for example the numbers of parity errors.
PPI/MPI/Profibus up to 12Mbit/s
view of variables in web browser with
setpoint monitoring and e-mail-alerts
|9352-WATCHDOG||Option Watchdog |
controlling of the connected MPI-/Profibus
with webbrowser or over port
|9350-9-CHP-CC||Option CheapConn for MPI|
9350-9-CHP+9350-9-CHP-K already mounted
|9350-9-CHP-K||Connecting cable MPIx to CheapConn|
9-pins 1 : 1 plated-through with shield
for MPI/PPI + MPI-II + MPI-USB
|9352-104||MPI-PC104-card 1 channel up to 12Mbaud Obsolete|
equates to PC104-standard (90.2 x 95.9mm)
|9352-104-2||MPI-PC104-card 2 channel up to 12Mbaud Obsolete|
equates to PC104-standard (90.2 x 95.9mm)
|9352-24||Power connector 2pins small|
cable coupling by screw-connector (small)
|9352-RS485-SK||Stub-compensator without galv. separation|
|9361-7||T-Connector to PPI / MPI-Bus|
doubling of PPI/MPI/Profibus-port
without bus connector
|9391-HH||DIN-rail-holder for MPI/PPI|
quick and easy assembling on the cap rail
|9391-USB||USB-powercable for 24V DC, max. 3W|
USB-plug type A to 2 open braids
24V DC, maximum current: 125mA (for PC
|9391.1||24V DC power-supply unit 625mA|
Primary 110V - 240 VAC Euro+USA-plug